Answers were Sorted based on User's Feedback
Answer / mohamed
NPSH Available should be more than The Rquired NPSH.
I mean that the pressure at the suction eye of the impeller
should be more than the saturated pressure for the pumped
liquid otherwise the pumped liquid will start to evaporate
and cavitation problems will start.
i will mension here some reasons for cavitation:
- pump selection is not correct
-suction tank is not in a proper elevation.
- isolation valves are partially closed
- mesh size of pump strainer is not correct
- pump strainer is partially blocked
- the system is not vented in aproper way .
- tempertaure of pumoed liquid is deviated form normal
still many reasons are there , but finally you should keep
the pressure at pump suction more than saturated pressur.
|Is This Answer Correct ?||12 Yes||1 No|
Answer / mazher
For avoiding cavitation NPSH(Available) should be always
greater than NPSH(Required).
|Is This Answer Correct ?||7 Yes||1 No|
Cavitation takes place when liquid pressure falls below its
Vapour Pressure forming bubbles of liquid.
To avoid cavitation (NPSH)available > (NPSH)required.
We know that...
NPSH is Net Positive Suction Head.
NPSH = (H)atm - (H)vapour - (H) manometric
the above equation must come Positive value to avoid
|Is This Answer Correct ?||1 Yes||0 No|
How is propeller fitted in shaft?
bullet proof glass is made up of which material?
I am completed diploma in mechanical in 2002, i have 5year experience in materials (purchase) dept,i want to do SAP cource in MM module, i want to know can i complete SAP after diploma cource only, is it usefull to me for further Job opening.
please let me know the book for preparing to section engi and loco pilot bangalore
why we use charcoal layer in aqua silencer to purify the gases??
difference between 1st angle and 3rd angle projection
what is the dome assembly
what is the diff between c++ and java?
what is the use of CW(Circulating water ,clarified water,cooling water),auxiliary cooling water(ACW),auxiliary raw cooling water(ARCW)in thermal power plant.plzz explain the different characteristics of these types of water.
What is plant load factor?
Identify the common problems and solution for gas turbines, diesel generator and wind turbine during operation.
how does the belt tension is checked and what should be the tension?