how to given power supply of any type two wire transmitter
Answers were Sorted based on User's Feedback
Answer / visakh
input voltage is 24vdc
output is 4-20mA
|Is This Answer Correct ?||7 Yes||3 No|
Answer / bhaumik
In the 2-wire transmitter 24VDC power is given. The +ve of
the 24V is connect to +ve of the transmitter, -Ve of the
transmitter is connect to +ve of the Indicator & -ve of the
indictor is connect to -ve of the 24Vdc powersupply.
|Is This Answer Correct ?||7 Yes||4 No|
Answer / manoj kumar
A two wire transmitter is connected directly to the wires
coming from DCS/PLC with (+)ve to the (+)ve terminal of the
transmitter and (-)ve to the (-)ve terminal of the
|Is This Answer Correct ?||2 Yes||0 No|
Answer / touch2gobi
In 2 Wire system, we have only two terminals
1 - +24 Vdc
2 - Output signal (4 - 20mA)
No Need ground signal etc....
|Is This Answer Correct ?||3 Yes||3 No|
What is the difference between precision and repeatability of any instrument. Why it is measured always in percentage
Name different parts of a pressure gauge.
why we are using ungrounded RTD sensor and what is difference between grounded RTD and Ungrounded?
What is maintenance planning?
Why all the drains(Gland sealing,ESV,Casing inlet etc) are directly connected to the flash tank instead of hotwell of the condensor in the power plant? My Email Id:email@example.com
god evening sir i am studying m.sc(tech)electronics &instrumention.am i elegible to all industies
hw to calibration a control valve?
in yokogawa prosef rd safety PLC how to data send frome local SCS to other SCS and other FCS
What is the use of GMV in turbine?
what is PID n give me brief info. about P&I&D.
I am using Capacitive type level transmitter for measuring oil level in a closed tank (lub oil tank). The txs range is 1500mm, and they do hunt regularly (for about 45mm), can anybody tell what could be the reason??? or any other type level tx that could be used to avoid this?
how to calibrate TT transmitter