Follow Our FB Page << CircleMedia.in >> for Daily Laughter. We Post Funny, Viral, Comedy Videos, Memes, Vines...

Are same transformer be employed for step up and step down
services?

Answers were Sorted based on User's Feedback

Are same transformer be employed for step up and step down services?..

NO
same transformer can't be used for both operations.
exception is ICT like 220KV/400KV
ICT is inter connecting or interposing transformer, these type of transformers are specially designed.
there no load an on load losses ane calculated so that they can be operated from either side.

on the other hand if have a 2000 KVA 11kv/440V 0.85 pf step down transformer:
current in hv side will be = 123 A
and current in LV side will be =3087 A

the secondary has to bear heavy current so it is designed accordingly with Thick winding.
and HV Primary has to carry a comperatively low current so its windings are of thin windings.

NOW the reverse operation

the heavy winding will be connected to high Voltage 11 Kv side, fine no problem, because it has to carry a lower current of 123 A ans secondary is rated for 3500 A approx.

BUT
the thin wired high voltage winding will now have to supplly the larger gurrent 3080 A, this winding has also larger losses R=Rho L/A
result??
the winding will burn out.

so practically it is not possible.

 Is This Answer Correct ? 2 Yes 0 No

Are same transformer be employed for step up and step down services?..

Strictly speaking No.

Most transformers rated above 3kVA can be used either as
step up or as step down depending upon the need.

But transformers rated below 2kVA can be used only for one
operation for which it is designed.It can not be employed
in revese(with respect to design) transformation,because
the winding used is compensated which will not work
satisfactorily in reverse.

Author:arbelectbit@yahoo.com

 Is This Answer Correct ? 1 Yes 1 No

Are same transformer be employed for step up and step down services?..

if we are using the same rating of transformer for same line
then only we can use it in both the ways otherwise if u say
that the distribution transformer can b used as a power
transformer just by changing its primary to secondry or vice
versa its not possible.
a transformer is the only device which can b used in step up
and step down both the ways.

 Is This Answer Correct ? 0 Yes 2 No

More Electrical Engineering Interview Questions

I meggared my 2c*70 sq mm AL AR XLPE cable. its one end show 50 M ohm . is my cable is safe for laying. I have only one phase and neutral.

xfhnchncv?

1.4 What is meant by CT knee point voltage and how would you determine it

what is the difference between 4pole & 6pole DC Motors & give advantage ?

Why earthing done?

the single phase voltage is 230 volts and threee phase is 430 v.why three phase is not 660 v?

What is the different between conventional MCC and intelligent MCC? Common controller or controller for each bucket

Why dnt we generate 5-ph or 7-ph supply like as 3-ph supply

1. If 8.35%Z means the percentage impedance of 132kV-line from power company, we will like to confirm its base capacity?

what is entropy?

How impulse levels are calculated that for 11kV impulse is 75kvp, for 24kV impulse is 125kvp ?

why do transformer humm ??????????

Categories
• Civil Engineering (5074)
• Mechanical Engineering (4444)
• Electrical Engineering (16594)
• Electronics Communications (3915)
• Chemical Engineering (1092)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2986)
• Automobile Engineering (332)
• Mechatronics Engineering (97)
• Marine Engineering (123)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1377)