What is the purpose of taking Capacitance and Tan Delta
Answer / dinesh lokhande
Transformer bushings OIP (Oil impregnated paper) consist of
paper foil surrounig conductor which termiantes at test tap
and oil is filled in between paper. This arrangement is
equivlent to no of capacitances in series.
To check healthiness of deielectric we conduct Capacitance
Tan detla test from specially designed apparatus which
gives values of capacitance and tan delta which can be
compared to Factory test results and designed values.
Vector disagram is as shown below.
In above vector we can explian as follows.
From property of ideal capacitor currnet vector Ia leads
Voltage vector V by 90 deg.
However due to dielctric losses, Calculated or charging
current Ic lags behind actual current by angle delta (D -
dielctric loss angle).
Hence Tan delta calculated is dielectric loss.
|Is This Answer Correct ?||22 Yes||5 No|
Which types of gate insttaled in static switch. Please give me answer.
Are Refrigerators & Deep Freezers the Inductive load ? How to calculate the Power Factor & hence the Output Power for them ?
I If i have 2kv ups in which 38Amp *8battries hou many hour's back up i get from 600Watts
What is the purpose of REACTOR in GIS substation?
What are the different auxiliary protections of a transformer?
how many power plants in andhra pradesh,how many types and there capacity
how to find the transformer neutral copper earthing size
if any body have question paper of railway (section engineering),then plz send me .i will thank of him/her.
how to get bearing & winding temperature of an induction motor?
What is Diff btw Fire Alarm & VESDA System???
how many types of accuracy class in ct? what is meaning of 5p20?
I COMPLITED MY B.TECH AND 10TH CLASS WITH 70%MARKS BUT 12TH CLASS 55%MARKS..CAN I GET INDIAN RAILWAY RECUREMENT EXAMINATION?