what is the design voltage for 6.6KV 2000 KVAR HT capacitor?
Answer / altaf
It is 7.2kV. This is arrived by taking into account 10%
increase in supply voltage & rounded off. However this is
for installation where series reactors are not used. In
case a reactor is used (6% for HT) then the design voltage
is 6.6x1.1/(1-6/100) = 7.72kV. The design kVAr also needs
to be increased accordingly otherwise the output is reduced
and detuning percentage changes & detuning frequency
|Is This Answer Correct ?||0 Yes||0 No|
what is the difference b/c choke and ballast?
why do we connect voltmeter in parallel,why not in series,and why do we connect ammeter in series why not in paprallel...
what's the simultenous maximum demand (SMD)..what the diffrent MD and SMD?
difference between a diode and thyristor?
what is the setting of locked rotor in HT motor ? (answer expecting in percentage)
if we want ot select cable size with reference to load current it take than what is the formula and it is same for aluminium or copper?
1. What kVA rating is required for a transformer that must handle a maximum load current of 8 A with a secondary voltage of 2 kV?
what is the difference between indoor package substation and outdoor
if 40 watt bulb has higher resistance then a 100watt bulb then according to joul farmula p=I^2R the 40 watt bulb more power consume then 100 watt bulb.
difference between substation & grid substation?
what is the clearance time circuit breakr?
How to calculate incoming cable size for 33KV, 1MVA transformer.