HOW TO CALCULATE CT AND VT RATIO IN PRTECTION AND METERING?
Answer / naveen singh
To find out Multiflying factor
1) If meter CT Ratio is not given then CT Ratio provided in
the panel has to be considered. Example if CT Ratio in the
Metering Panel is 600/5 then the M.F is 120.
2) If CT Ratio is mentioned in the Meter then Meter CT
Ratio / CT Rating Provided in the Metering panel.
Example If the CT Ratio of the Meter is 600/5 and CT
Provided in the Panel 800 /5 then Multiplying Factor will
be 600/5 /800/5. i.e., 600/800 then M.F is 3/4 (0.75)
3)In addition to this any Multiflying factor is mentioned
in the Meter then it has to be multiplied. Example if Meter
CT Ratio is 600/5 and Panel Ratio is 800/5 and M.F
mentioned in the Meter is 3 then the M.F will be (600/800)
*3. i.e., 0.75*3 =2.25
|Is This Answer Correct ?||20 Yes||8 No|
why it is unable to birds to be on a 220kV 0r 132 kv lines like on 33kV and 11kV lines?
what is booster? and how it is connected in a circuit?
how can testing using megger?
What should be setting for alarm,tripping and cooling fan on for power transformer's oil temp. and winding temp. indicator?
What is auto changeover and how it works plz write details.
How can i calculate the Breaking capacity of molded case circuit breaker, is the breaking capacity of CB for Diesel generator shall be less than grid supply's breaker ?
what is difference b/t ac current and dc current
what is POTT and PUTT explain?
Why a transformer is known as a static device?
EHV current carrying parts need to have smooth finish,then how can a 245kv GIS with emery finish can run so long?
what is the differance of acb and mcb and mccb
draw singleline diagram of star to delta and dol starters