1.What is wind span ,wight span and normal span, and what is the difference for 132kv transmission .
*The wind span is that on which the wind is assumed to act transversely on the conductors and is taken as half the sum of the two spans, adjacent to the support.In order to take full advantage of towers located on elevated ground, it is usual to allow a wind span of 10 to 15 percent in excess of
the normal span. This additional strength can be used in taking a samll angle of deviation on an intermediate tower, where the actual wind span is less than the design wind span. The angle of deviation to be taken in such cases is approximately given by:
θ =( wl /π T )x x180
Where w = total ind load per unit run of span length of all conductor
carried by the tower,
l = difference between the wind span used for design and the actual
wind span, and
T = the total maximum working tension of all conductors carried by the
*The weight span is the horizontal distance between the lowest point of the conductors, on the two spans adjacent to the tower . The lowest point is defined as the point at which the tangent to the sag curve, or to the sag curve produced, is horizontal. The weight span is used in the design of cross-arms.
|Is This Answer Correct ?||0 Yes||0 No|
What is the Polarisation index value ? (pi value)and simple definition of polarisation index ?
we often use the word HT (high tension) line.or we say HT switch gear, whats does HT basically mean. is it different from high voltage.
what is sustainable current of any conductors . a bare busbar or pvc cable has different sustainable current .
how to calculate the size of the HT cable
We have 2 11kv/433v transformers for 2saperate acb for mv panels and 1 bus coupler acb. Suppose I’ll close bus coupler what will happen or it will be share the load. Please suggestion and any modification required.
how to find 5 kilo meter long under ground 33 kv cable fault location if IR VALUE shows 0.05 M ohm @5000 volt.and cable fault locator shows some time fault distance 3 kilo meter ,3.7 kilo meter and some time 1 kilo meter? now how to find the fault location that where is leakage.
How do you select a cable size(cu and Al) for a particular load
what is the VA(Volt-amphere)? define with calculation?
what do you mean by leading power factor & lagging power factor
Match the following a)(X'+Y') b)X'Y' C)XY 1)NAND 2)NOR 3)Carry
what are ABCD curves in MCBs and how we observe that curves?
If a high resistance fault occurs,then what are the changes will happen in the system?