what is percentage impedance of transformer? explain its
significance

Answers were Sorted based on User's Feedback

what is percentage impedance of transformer? explain its significance..

percentage or per unit impedance = (Acutal impedance of the
transformer) divided by Base impedance .
1) The percentage impedance basically defines the short
circuit capability of the transformer bcoz short circuit
current is inversely proportional to the p.u impedance of
the system.
2) Secondly, it defines the voltage regulation of the
transformer bcoz max. voltage regulation is directly
proportional to the p.u impedance of the transformer.

So a high p.u impedance will reduce the short circuit level
and on the other it will result in poor voltage regualtion.
And a low p.u impedance will result in higher short circuit
level and good voltage regulation.

So the transformer are usually designed with a moderate p.u
impedance of say 5.75% to 8.75% to achieve both the low
short circuit level and good voltage regulation.

 Is This Answer Correct ? 13 Yes 2 No

what is percentage impedance of transformer? explain its significance..

The impedance of a transformer is defined as the percentage of the drop in voltage to the at full load to the rated voltage of the transformer. This drop in voltage is due to the winding resistance and leakage reactance.
Alternatively, the percentage of a transformer can be described as the percentage of the nominal voltage in the primary that is required to circulate the rated current in the secondary.

 Is This Answer Correct ? 12 Yes 3 No

More Electrical Engineering Interview Questions

How to justify this statement ??? "Capacitors in series provide less capacitance but higher voltage breakdown rating for the combination"

how can i use REF and diffrencial relay both in 1 CT core for transformer protection?

what is ac servomotor??

if vcb make contact but output notreach give the reason?

why we use Test Terminal Block in 11 KV and 33 KV electrical panels.

What is the difference between the transmission line and distribution line?

What is the effect on 3phase induction motor if current setting knob of DOL kept at minimum current?

an amazing situation was faced when an alive distribution panel with 415 volts and carrying almost 200Amps has become short and this metal cubical showing 220 volts against neutral and earth. to redress any confusion i checked the panel with help of single 200watts test lamp which also glowing with max.intensity b/w neutral & metal body of DB. amazing situation is that i hold the DB firmly more than once with necked foot means without insulated shoes but not received any electrical shock. whereas our all running gen sets neutral points also proper grounded and this short DB was completely earthed , this is beyond my understanding . any body explain how is it possible . our running gen set neutral also grounded firmly

WHAT IS B & C CLASS SURGE PROTECTION AND WHAT IS DIFFERENCE BETWEEN B & c CLASS SP

please send me previose rrb junior engineer qustion papers

How will you calculate the correct KWH value if your CT is 600/5 and your KWH meter is rated for 100/5

what is the use of sdf?

Categories
• Civil Engineering (5069)
• Mechanical Engineering (4437)
• Electrical Engineering (16571)
• Electronics Communications (3914)
• Chemical Engineering (1091)
• Aeronautical Engineering (214)
• Bio Engineering (96)
• Metallurgy (361)
• Industrial Engineering (258)
• Instrumentation (2984)
• Automobile Engineering (332)
• Mechatronics Engineering (96)
• Marine Engineering (122)
• Power Plant Engineering (170)
• Textile Engineering (575)
• Production Engineering (0)
• Satellite Systems Engineering (106)
• Engineering AllOther (1376)