The surge impedance loading or SIL of a transmission line is
the MW loading of a transmission line at which a natural
reactive power balance occurs. The following brief article
will explain the concept of SIL.

Transmission lines produce reactive power (Mvar) due to
their natural capacitance. The amount of Mvar produced is
dependent on the transmission line's capacitive reactance
(XC) and the voltage (kV) at which the line is energized.
In equation form the Mvar produced is:

Transmission lines also utilize reactive power to support
their magnetic fields. The magnetic field strength is
dependent on the magnitude of the current flow in the line
and the line's natural inductive reactance (XL). It follows
then that the amount of Mvar used by a transmission line is
a function of the current flow and inductive reactance. In
equation form the Mvar used by a transmission line is:

A transmission line's surge impedance loading or SIL is
simply the MW loading (at a unity power factor) at which the
line's Mvar usage is equal to the line's Mvar production.
In equation form we can state that the SIL occurs when:

If we take the square root of both sides of the above
equation and then substitute in the formulas for XL (=2pfL)
and XC (=1/2pfC) we arrive at:

The term in the above equation is by definition the "surge
impedance. The theoretical significance of the surge
impedance is that if a purely resistive load that is equal
to the surge impedance were connected to the end of a

transmission line with no resistance, a voltage surge
introduced to the sending end of the line would be absorbed
completely at the receiving end. The voltage at the
receiving end would have the same magnitude as the sending
end voltage and would have a phase angle that is lagging
with respect to the sending end by an amount equal to the
time required to travel across the line from sending to
receiving end.

The concept of a surge impedance is more readily applied to
telecommunication systems than to power systems. However,
we can extend the concept to the power transferred across a
transmission line. The surge impedance loading or SIL (in
MW) is equal to the voltage squared (in kV) divided by the
surge impedance (in ohms). In equation form:

Note in this formula that the SIL is dependent only on the
kV the line is energized at and the line's surge impedance.
The line length is not a factor in the SIL or surge
impedance calculations. Therefore the SIL is not a measure
of a transmission line's power transfer capability as it
does not take into account the line's length nor does it
consider the strength of the local power system.

The value of the SIL to a system operator is realizing that
when a line is loaded above its SIL it acts like a shunt
reactor - absorbing Mvar from the system - and when a line
is loaded below its SIL it acts like a shunt capacitor -
supplying Mvar to the system.

Figure 1 is a graphic illustration of the concept of SIL.
This particular line has a SIL of 450 MW. Therefore is the
line is loaded to 450 MW (with no Mvar) flow, the Mvar
produced by the line will exactly balance the Mvar used by
the line.

Please Help Members By Posting Answers For Below Questions

Question

Views

Select

the grid connection required for a 50 MegaWatt fotovoltaic
powerplant is higher or lower than 35kv (high or medium
tension)?

274

please send me jindal previous aptitude and technical
question and answer.my email id is deep_raj@live.com

346

What are high pass filter and low pass filter? and What are
the flowmeter ?

380

What size cable (based on voltage drop) is required to
supply a 40 A three phase boiler if the wiring system is
75V single insulated cables installed in non-metallic rigid
conduit 56m from the main switchboard? Voltage drop in the
consumer's mains is 8V.

390

which network topology offers the greatest level of
tolerance?

405

can anybody sent me power grid questions. what subject
should i prefer for preparation?

452

how to calculate mf when meter and cTPT detail are given

138

Is any generator is developed which is operated with out
diesal or other expensive source?

400

plz send me the placement interview question and answers of
whizchip(technical and apttitude)..i have an interview in
next.

727

th how could we differentiate between armoured copper and
armoured aluminium cable what is the basic application?
why we prefer the armoured copper as compared to armoured
aluminium.

357

at meter room 50 hrc switch installed,but there are not get earthing proper,so what happen?and 11kv transformer out put going in to hrc main 400a three nog each? so earthing is require for all switch? (some customer made earthing at there home.)

426

hi frnds what is meant by harmonics & what is meant by third
hormonics,where its will occur ?thank u

404

What is difference between slip rings and carbon burushes?

8026

how we can find of current direction(supply comming/out
going direction) when a transmission line passing through
sides.

567

Where can I get CPWD electrical specifications & Shedule of
rates? Please help me