The surge impedance loading or SIL of a transmission line is
the MW loading of a transmission line at which a natural
reactive power balance occurs. The following brief article
will explain the concept of SIL.

Transmission lines produce reactive power (Mvar) due to
their natural capacitance. The amount of Mvar produced is
dependent on the transmission line's capacitive reactance
(XC) and the voltage (kV) at which the line is energized.
In equation form the Mvar produced is:

Transmission lines also utilize reactive power to support
their magnetic fields. The magnetic field strength is
dependent on the magnitude of the current flow in the line
and the line's natural inductive reactance (XL). It follows
then that the amount of Mvar used by a transmission line is
a function of the current flow and inductive reactance. In
equation form the Mvar used by a transmission line is:

A transmission line's surge impedance loading or SIL is
simply the MW loading (at a unity power factor) at which the
line's Mvar usage is equal to the line's Mvar production.
In equation form we can state that the SIL occurs when:

If we take the square root of both sides of the above
equation and then substitute in the formulas for XL (=2pfL)
and XC (=1/2pfC) we arrive at:

The term in the above equation is by definition the "surge
impedance. The theoretical significance of the surge
impedance is that if a purely resistive load that is equal
to the surge impedance were connected to the end of a

transmission line with no resistance, a voltage surge
introduced to the sending end of the line would be absorbed
completely at the receiving end. The voltage at the
receiving end would have the same magnitude as the sending
end voltage and would have a phase angle that is lagging
with respect to the sending end by an amount equal to the
time required to travel across the line from sending to
receiving end.

The concept of a surge impedance is more readily applied to
telecommunication systems than to power systems. However,
we can extend the concept to the power transferred across a
transmission line. The surge impedance loading or SIL (in
MW) is equal to the voltage squared (in kV) divided by the
surge impedance (in ohms). In equation form:

Note in this formula that the SIL is dependent only on the
kV the line is energized at and the line's surge impedance.
The line length is not a factor in the SIL or surge
impedance calculations. Therefore the SIL is not a measure
of a transmission line's power transfer capability as it
does not take into account the line's length nor does it
consider the strength of the local power system.

The value of the SIL to a system operator is realizing that
when a line is loaded above its SIL it acts like a shunt
reactor - absorbing Mvar from the system - and when a line
is loaded below its SIL it acts like a shunt capacitor -
supplying Mvar to the system.

Figure 1 is a graphic illustration of the concept of SIL.
This particular line has a SIL of 450 MW. Therefore is the
line is loaded to 450 MW (with no Mvar) flow, the Mvar
produced by the line will exactly balance the Mvar used by
the line.

Please Help Members By Posting Answers For Below Questions

Question

Views

Select

what is sevice settings for mccb?How can be it setted?

233

what type questions asked in hp cl

328

what are factors to be consider to design a HT & LT motor?

556

Explain the different methods used in the choice of rotor
slots for reduction of
harmonic torques in an induction motor.

210

I am interested to know what does 15 KVA DG set actually
means? If I dont know the DG rating, is it possible to
identify KW by simply knowing the diesel consumption?

446

How to test the vector group of a Yd11 transformer? what
are the relations to be checked between various vectors to
confirm this vector group?

1995

If a current -8+6sin6t is flowing three ammeter, one is a
centre zero PMMC meter, one is true rms meter and one is
moving iron meter. What are the reading of these three meter
respectively?

279

what a function diesel generetaor turbo charger & turbo
charger is more heated explain reason ?

552

WHAT IS SPEC OF CLEANROOM MOTOR AND LIGHT FITTINGS?

386

15HP,380V,31AMP,3-PH SUBMERSIBLE MOTOR RUN AT 250V WHAT IS
THE TEMPERATURE RISE OF SUBMERSIBLE MOTOR

457

How eddy current generation support the idea of train braking?

261

Write down the name of 2 lady Bir Pratin of Bangladesh

295

define displacement & magnitude ?

246

What is the rating factor for copper cable ( Specific value
according to the type of laying ) & the voltage drop?

281

Match the following
a)(X'+Y') b)X'Y' C)XY
1)NAND 2)NOR 3)Carry