The surge impedance loading or SIL of a transmission line is
the MW loading of a transmission line at which a natural
reactive power balance occurs. The following brief article
will explain the concept of SIL.

Transmission lines produce reactive power (Mvar) due to
their natural capacitance. The amount of Mvar produced is
dependent on the transmission line's capacitive reactance
(XC) and the voltage (kV) at which the line is energized.
In equation form the Mvar produced is:

Transmission lines also utilize reactive power to support
their magnetic fields. The magnetic field strength is
dependent on the magnitude of the current flow in the line
and the line's natural inductive reactance (XL). It follows
then that the amount of Mvar used by a transmission line is
a function of the current flow and inductive reactance. In
equation form the Mvar used by a transmission line is:

A transmission line's surge impedance loading or SIL is
simply the MW loading (at a unity power factor) at which the
line's Mvar usage is equal to the line's Mvar production.
In equation form we can state that the SIL occurs when:

If we take the square root of both sides of the above
equation and then substitute in the formulas for XL (=2pfL)
and XC (=1/2pfC) we arrive at:

The term in the above equation is by definition the "surge
impedance. The theoretical significance of the surge
impedance is that if a purely resistive load that is equal
to the surge impedance were connected to the end of a

transmission line with no resistance, a voltage surge
introduced to the sending end of the line would be absorbed
completely at the receiving end. The voltage at the
receiving end would have the same magnitude as the sending
end voltage and would have a phase angle that is lagging
with respect to the sending end by an amount equal to the
time required to travel across the line from sending to
receiving end.

The concept of a surge impedance is more readily applied to
telecommunication systems than to power systems. However,
we can extend the concept to the power transferred across a
transmission line. The surge impedance loading or SIL (in
MW) is equal to the voltage squared (in kV) divided by the
surge impedance (in ohms). In equation form:

Note in this formula that the SIL is dependent only on the
kV the line is energized at and the line's surge impedance.
The line length is not a factor in the SIL or surge
impedance calculations. Therefore the SIL is not a measure
of a transmission line's power transfer capability as it
does not take into account the line's length nor does it
consider the strength of the local power system.

The value of the SIL to a system operator is realizing that
when a line is loaded above its SIL it acts like a shunt
reactor - absorbing Mvar from the system - and when a line
is loaded below its SIL it acts like a shunt capacitor -
supplying Mvar to the system.

Figure 1 is a graphic illustration of the concept of SIL.
This particular line has a SIL of 450 MW. Therefore is the
line is loaded to 450 MW (with no Mvar) flow, the Mvar
produced by the line will exactly balance the Mvar used by
the line.

Please Help Members By Posting Answers For Below Questions

Question

Views

Select

what happen if the supply is given to the stator of the 3phase
induction motor with out assembling the rotor ?

364

where are the circulat the diesel in DG parts name with
pictue

518

what is the reason the main breaker is trip during the motor is running? (some time the breaker is not trip)

236

What is a difference between indoor transformer and outdoor transformer of same rating

303

hi frnds can any one help me ? plz send me placement paper
of IOCL of Electrical streem .... plz send ....its urgent....

224

Q: How to calculate Transformer losses , tell us by Formula.

393

please send the IS strandard for electrical to
sakthi_murugan86@yahoo.co.in

675

What is the range of the stator resistance of 3 phase
induction motor?

380

Dear friends, i would like to know that what is the exact
function of 'exciter winding' & 'aux winding' in Alternator?

371

what is the minimum recommended leakage current of an
earthed cable connected to the body or skid of an alternator

334

how to avoid electrical shock
how capacitor store charges
wat are the speed control of induction motors
state faradays law
flemings left hand rule
what is rotary converter
wat is transmission and distribution
what are the sources of energy
abrevation of acb,vcb,sf6,igbt
what is output equation of transformer
which test copper iron and iron loss are calculated
what is eddy current
draw a single line diagram (10 marks)
draw direct online starter(10 marks)

393

diameter of cable and core is doubled then the value of
capacitance is

780

Why are cables rated for 40 KA for 0.25 Sec fault current
rating?

347

we have a rewind motor of 2Hp,2800Rpm, 220Volt AC. how can
we choose the running capacitor for this motor, any formula
for that?