The surge impedance loading or SIL of a transmission line is
the MW loading of a transmission line at which a natural
reactive power balance occurs. The following brief article
will explain the concept of SIL.

Transmission lines produce reactive power (Mvar) due to
their natural capacitance. The amount of Mvar produced is
dependent on the transmission line's capacitive reactance
(XC) and the voltage (kV) at which the line is energized.
In equation form the Mvar produced is:

Transmission lines also utilize reactive power to support
their magnetic fields. The magnetic field strength is
dependent on the magnitude of the current flow in the line
and the line's natural inductive reactance (XL). It follows
then that the amount of Mvar used by a transmission line is
a function of the current flow and inductive reactance. In
equation form the Mvar used by a transmission line is:

A transmission line's surge impedance loading or SIL is
simply the MW loading (at a unity power factor) at which the
line's Mvar usage is equal to the line's Mvar production.
In equation form we can state that the SIL occurs when:

If we take the square root of both sides of the above
equation and then substitute in the formulas for XL (=2pfL)
and XC (=1/2pfC) we arrive at:

The term in the above equation is by definition the "surge
impedance. The theoretical significance of the surge
impedance is that if a purely resistive load that is equal
to the surge impedance were connected to the end of a

transmission line with no resistance, a voltage surge
introduced to the sending end of the line would be absorbed
completely at the receiving end. The voltage at the
receiving end would have the same magnitude as the sending
end voltage and would have a phase angle that is lagging
with respect to the sending end by an amount equal to the
time required to travel across the line from sending to
receiving end.

The concept of a surge impedance is more readily applied to
telecommunication systems than to power systems. However,
we can extend the concept to the power transferred across a
transmission line. The surge impedance loading or SIL (in
MW) is equal to the voltage squared (in kV) divided by the
surge impedance (in ohms). In equation form:

Note in this formula that the SIL is dependent only on the
kV the line is energized at and the line's surge impedance.
The line length is not a factor in the SIL or surge
impedance calculations. Therefore the SIL is not a measure
of a transmission line's power transfer capability as it
does not take into account the line's length nor does it
consider the strength of the local power system.

The value of the SIL to a system operator is realizing that
when a line is loaded above its SIL it acts like a shunt
reactor - absorbing Mvar from the system - and when a line
is loaded below its SIL it acts like a shunt capacitor -
supplying Mvar to the system.

Figure 1 is a graphic illustration of the concept of SIL.
This particular line has a SIL of 450 MW. Therefore is the
line is loaded to 450 MW (with no Mvar) flow, the Mvar
produced by the line will exactly balance the Mvar used by
the line.

Please Help Members By Posting Answers For Below Questions

Question

Views

Select

what is impedence of transformer?
its formula

308

We have 5 Distribution sections with variable loads&We have
3 Gensets(500kva,380kva&250kva) our total load is between
400kva to 600kva. so how could we connect 3gensets.

209

Whar is the KvA rating of 33Kv substation & actual kv
rating of power generaating station.

624

The capacitive reactance of a capacitor of 1/(2(PI)) F at
10^3 H is

318

If I want to lift the water at a height 50m from ground
level through two inch(diameter) metal pipe then what is
the capacity of motor pump is required? is it possible in
single phase supply or not?

293

LET ME NOW MORE ABOUT icu and ics for circuit breaker. how
we calculate the rating of circuit breaker and i c u and
ics values

986

sir iam a 3rd yr eee student.no core company comes for
recruitment to our college.my aim is to be placed in l and
t.tell me the procedures.

262

What should be the length of transmission line so that we
can see/obtain the full sine wave of voltage??

290

Please tell me the earthing procedures adopted for the
STAR-STAR 3 Phase transformer in india and give a better
sugession for earthing

307

what is the purpose of slope in the differential relay?why
we are using two slope?but in busbar differential we are
using only one slope.why?

936

Difference between earthing & grounding.?

242

WHAT IS THE CURRENT CARRYING CAPACITY OF 2.5/3 CORE HI TUFF
CABLE,WILL IT SAFLEY CARRY 8.6 AMPS OVER 120 METRES,CAN YOU
ALSO ANSWER WITH FORMULA FOR WORKINGS OUT ,THANK YOU 3RDYR
APPRENTICE.

1225

-What shall be short circuit current of LV switchgear for a
1000 kva, 11.415kv, 3 phase tranformer with 5% reactance.

516

"TRANSFORMER MODELING AND ANALYSIS" MEANS WHAT AND WHICH
TOPICS U READ IN THIS

214

In diesel generator how AVR get voltage to excitation. And basic diagram DG EXCITATION CIRCUIT.