An 11kv system consisting of an underground cable to a sub
station about 300 meters away was shut down for about 10
hrs. On energising, it tripped off on earth fault about
10---20 mins later 6 times but since than it is not
tripping.its already 3 weeks now. The SPAJ was found to be
fine. what could be the cause.No test had been done to
determine the cause of the trippings till now because of
Answer Posted / k.prakashchandra
If only you had replaced the breaker cubicle and test
charged you would have come to conclusion.If the all 3 poles
do not close almost at the same time and there is a time
gap, the breaker is likely to trip on EFR due to the
unbalanced current in case of 2 OCR + 1 EFR protection
scheme.In such cases it is advisable to test charge on no
load during the second time and confirm the mechanical fault
which is not consistent & does not occur always.
|Is This Answer Correct ?||1 Yes||0 No|
why the earth is taken minimum in supplying? wather it the proportional factor to getting work any equipment or a power plant?
What are the types of windings present in the ceiling fan? What winding will be effective first when we started the fan?What are the resistance and inductance ratios comparatively at the initial speed and full speed of the fan?
How many lightning arrestors to be installed on 50MX60MX10M building and is there any formular for that?
Define bibo stability.
How to synchronization will be done between two DGs ?
Pls tell me whether we can use EN3A material for shafts of Permanent magnet alternator.What will be the effect of magnetic and nonmagnetic material for shafts on magnetic properties of PM rotor .
What is the use of bundle conductors?
distribution is maximum done by a)radial b)network c) parallel d)b & c
how to test YNyn0 vector group in transformer?
How to convert 2 phase to 3 phase electricpower in induction moter?
direction of tarbine& genrator
he compression ratio for a petrol engine generally lies between
Where is the best place to mount distribution panel in a house.
Distribution transformer we provided 2 separate earthing pit for Body and 2 separate earthing pit for neutral,we can not connect separate body earthing pit to other earthing pit but we do metal glanding in secondary side cable termination in both side, transformer and PCC panel (LT Panel), is this safe for transformer and other equipment?
we all know voltage is a force(emf), and the force always devides if 2 or more than2 loads are there but why does the voltage remains same is parallel, it must devide na ???