Between AC generator(alternator) and DC generator which can
be designed for high voltage and why?
Answer Posted / iamdon
AC generator(alternator) can be designed for higher voltage
as compared to DC generator for following reasons.
Large rated alternators are of rotating field
type.i.e,armature is placed on stator which is stationary
and DC field winding is placed on rotor which is moving at
synchronous speed at steady state.
1)Insulation required for armature, is not subjected to any
mechanical stresss because of no rotation of armature.So
insulation for higher voltage is possible.
2)Armature is placed on stator which is outside.There are
more spaces available on armature.So it is easier to
provide more insulation for higher voltage withstanding
DC generator are of rotating armature type due to which above
mentoined beauty is less effective.So insulation for higher
voltage is not easier.
|Is This Answer Correct ?||8 Yes||1 No|
can mini-curcuit supply MIL-tested transformer !
explain the what is a drive ? 0 4 which type motor r use in the celling fan..... PCB plannet 2 13 If stator & rotor of a 3-phase induction motor have different no. of poles, will the motor run or not?? types of drives Why dc supply is used for closing and tripping coil of ht breakers. What happen if we use only ups ac supply only. ACC 1 41 how the 3phase induction motor is running in 2phase supply with help of capacitor? 1 33 what is the actual difference betwen constructional details and constructional features? 1 20 how does commutator convert a.c to d.c?
In our plant we have installed new MCC with ELR and CBCT which is detecting some leakage current in the system but it leading to some confusion when to check that in which feeder which is drawing current we put off the whole panel itself but still CBCT detecting some leakage current so can anybody ans me , where i am going wrong or how to detect whether its actual leakage or CBCT malfunctioning.
whatare the disadvantages occur,if the form factor of transmission will not be equal to 1.11
What is meant by reactance voltage?
in indoor type circuit breakers why only the corner breaker trips specially during cold season. What is the reason.
what is strip power factor?
what is sevice settings for mccb?How can be it setted?
how to test and calculat the head and discharge in borewell compressor
How grounding is different than earthings?
When color of silica gel will gets change from blue to pink from Top to bottom?
we can run 2phase as 3phase .what will be the differnce with respect to phase angle, power, current between the two modes
which is chemical used as in ro water what is difference betweeen multi grade filter&dual media filter
how balanced in star delta connection ?
what are the things that can cause a three phase motor to crawl?