how winding temperature detects in power transformer...?
Answers were Sorted based on User's Feedback
Answer / ullas
a special CT(current transformer ) is used to measure the
winding temperature in a power transformer.
the method is very simple, there will be one winding
temperature measurement pocket in the transformer. in this
a temperature measurement device is dipped and this pocket
will be filled with transformer oil. this special CT will
give output in the form of current which is proportional to
i think this makes a clear picture.
|Is This Answer Correct ?||23 Yes||5 No|
Answer / packyaraj
winding ct is provided on the LV side of the Power Transformer. This winding ct is connected to the winding temperature indicator with a resistor at WTI end.This resistor produce heat proportional to the circulating current due to heat produced in the winding. WTI dipped in the oil of the power transformer which measures the heat produced in the oil. WINDING TEMPERATURE = HEAT PRODUCED IN THE OIL + HEAT PRODUCED IN THE RESISTOR DUE TO WINDING CT. Usually for power transformer winding temperature Alarm set at 85 degree celsius and trip at 90 degree celsius.
|Is This Answer Correct ?||13 Yes||1 No|
Answer / gunjan
winding temp. is detected with the help of resistance
temperature detectors, that form a part of X-mers
|Is This Answer Correct ?||6 Yes||6 No|
Answer / nagaraju.n (bush king)
power transformer winding temperature detected by using
tempreture gauge (it is part of the transformer)
|Is This Answer Correct ?||5 Yes||13 No|
What is the use for cable entry in control room?
why is the vector group analysis done in transformer tests
what is difference between armoured cable and un armoured cable
Why USe In -48 DC Volt !
why we are useing capciter in EB meter?
Is ground earthing required for neutral conductor of a prime mover ie DG set?
What are the basic component of a cro?
Can we use droop CT in neutral in place of W phase of alternator ?
why fuse is not used in neutral...
why to need a electrical earthing?
a battery is having capacity 100AH and 25% charging .if a load taking 10A & connected 6 hour .what is the final condition of the battery.
Where the ON LOAD TAP CHANGER is provided in the setp up transformer?