If the current of one side either primary or secondary is
known than the current of other side will be in same
proportion as the volotage ratio of primary and secondary
For example -for a 1000 KVA 11kv/0.4 kv transformer if there
is 1 amp. current in HT side than current in LT side will be
1x11x1000/400 i.e almost 26 amps.
Let suppose u have taken 1500 kva transformer of 11kv to 415 v u wanna be the current calculation for the both HT side and LT side. But u also think that u have connect load of the transformer 1000 kw. In this case both HT & LT SIDE power drawn is same. But this is three phase so we take formula
P equal to SQ ROOT 3 *V* I COS phai
Remember cos phai is necessary becuse of we know KVA :::: KW/ COS phai
U have connect 1000kw and its drawn full lo
ad then it wil be calculate in HT SIDE
1000*1000:::1.732*11000*0.8* I(u take power factor as0.8)
WHILE calculating in LT SIDE IT wil be
1000*1000::: 1.732*440*0.8* I
because power drawn HT & LT SIDE depend on load connected to the transformer
is KVAR (not reverse power) relay necessary to protect from
excitor field failure on a brushless, synchroneus generator?
Some people with previos experince tell me no but the
manufacturers tell me it is designed for that purpose.
Is it that it is only necessary for brushless generators
and not the older style with the slip rings and brushes?