Browse  |   Placement Papers  |   Company  |   Code Snippets  |   Certifications  |   Visa Questions Post Question  |   Post Answer  |   My Panel  |   Search  |   Articles  |   Topics  |   ERRORS new
 Ask Questions on ANYTHING, that arise in your Daily Life at     FORUM9.COM

 Categories >> Engineering >> Electrical Engineering

 Civil Engineering Interview Questions (2983) Mechanical Engineering Interview Questions (3261) Electrical Engineering Interview Questions (13158) Electronics Communications Interview Questions (2344) Chemical Engineering Interview Questions (407) Aeronautical Engineering Interview Questions (76) Bio Engineering Interview Questions (16) Metallurgy Interview Questions (79) Industrial Engineering Interview Questions (162) Instrumentation Interview Questions (2307) Automobile Engineering Interview Questions (104) Mechatronics Engineering Interview Questions (38) Marine Engineering Interview Questions (43) Power Plant Engineering Interview Questions (69) Engineering AllOther Interview Questions (1185)
Question
`how to calculate the transformer losses.`
Question Submitted By :: Savan
I also faced this Question!!     Rank Answer Posted By

Re: how to calculate the transformer losses.
# 1
How to find out Iron & Copper lossed in transformer:-

1>Iron Losses:-
Iron losses are due to hysteresis and eddy-current loss
produced by the alternating magnetic flux in the iron core.
The iron losses are almost independent of the load and thus
are considered to be constant at all loads.

In order to determine the iron loss, one winding of the
transformer (whichever is the most convenient) is open
circuited. A voltage is applied to the other winding and
the power (watts) in this circuit is measured. This power
represents the iron losses. Copper losses under these
circumstances are negligible.

2>Copper Losses:-

Copper losses are the heat losses in the windings due to
the electrical resistance of the windings. The copper
losses are proportional to the square of the current and
therefore to the kVA output. These losses can be calculated
from the design data but can also be measured by a test.
This test is known as the short circuit test for copper
losses.

The short circuit test is carried out by short circuiting
one winding, thus causing the transformer to behave like a
coil having a leakage impedance equal to that of both
windings. A low voltage is applied to the open winding
sufficient to circulate full load current through the open
winding due to transformer action in the short-circuited
winding. Under these conditions, the flux set up in the
core is so small that iron losses can usually be neglected
and the wattmeter would give the total copper loss.

 Is This Answer Correct ? 35 Yes 5 No
Thwosif_emrson

Re: how to calculate the transformer losses.
# 2
hysteresis loss =Bmaxpower 1.6 fv
eddy current loss= Bmaxsqrfsqrtsqrv
B-flux density
f-frequency
t-thickness of the core
v-voltage
in this loss all are constant so core loss is almost const
so it is depending upon the load and the internal resistance
for high efficiency core loss=copper loss

 Is This Answer Correct ? 7 Yes 4 No
Maharajan

Re: how to calculate the transformer losses.
# 3
I think v is volume of the core not voltage.

Anyway, if someone know an accurate method to calculate
power losses in power transformer please tell me.

 Is This Answer Correct ? 5 Yes 2 No
Gabriel Pop

Re: how to calculate the transformer losses.
# 4
In transformer 2 types of losses
1.constant losses(core losses and eddy current losses)
this loses estimated by conducting open circuit test
in oc test we apply rated voltage .so we obtain total constant loses
2. variable losses (cu loses)
this loses estimated by conducting short circuit test.
in sc test we pass rated current through windings of transformer .so we get the rated copper losses.
cu losses vary with load but by conducting sc test we obtain max cu loss

 Is This Answer Correct ? 4 Yes 0 No
Arun

  Question Asked @ Answers Other Electrical Engineering Interview Questions From, which load current range ( upper - lower limit current)can Air circuit breaker used for in electrical circuit. ABC 4 Two electronic energy meters are connected to seperate phase wires, but connected to a looped neutral. Are these going to function correctly? DRDO 8 why ac supply neutral should earth not in dc (-) 2 Difference between 3.5 core and 4 core 2 In case of 11kV dual delta bank what are the recommended protections with specific CT / VT requirements? The capacitor bank is to be connected to the main 11kV switchgear from where the H.V.Motors and auxiliary 440V loads. 1 what is different between auto transformer and vriac 4 1.why is +1+1=+2 why cant it be +3 2.Why is +1*-1=-1 why cant it be something else 3.why are the hilly areas more cooler than the ordinary areas? ThyssenKrupp 5 As a good company employee, can you report your supervisor to the company management if he or she is going against the company interest in his or her actions? 2 Why is transformer connect parallel? why not series? ....plz... WBSEDCL 3 what is multiplying factor of a energy meter connected with a CT ratio of 600/5 and voltage at 415 volts. 1 why can't we provide dc supply to a transformer? 2 Will The Rated Capacity of 20 MVA ,220/6.6 KV, ONAN cooling Power Tranformer be increased up to 25 MVA with respect to its %Impedence by ONAF cooling with same rating..? Ambuja 2 For more Electrical Engineering Interview Questions Click Here