Browse  |   Placement Papers  |   Company  |   Code Snippets  |   Certifications  |   Visa Questions Post Question  |   Post Answer  |   My Panel  |   Search  |   Articles  |   Topics  |   ERRORS new

 Categories >> Engineering >> Electrical Engineering

 Civil Engineering Interview Questions (3076) Mechanical Engineering Interview Questions (3289) Electrical Engineering Interview Questions (13329) Electronics Communications Interview Questions (2363) Chemical Engineering Interview Questions (416) Aeronautical Engineering Interview Questions (77) Bio Engineering Interview Questions (17) Metallurgy Interview Questions (79) Industrial Engineering Interview Questions (163) Instrumentation Interview Questions (2378) Automobile Engineering Interview Questions (106) Mechatronics Engineering Interview Questions (38) Marine Engineering Interview Questions (43) Power Plant Engineering Interview Questions (77) Engineering AllOther Interview Questions (1196)
Question
`ups and invertor battery selection chart and full formula`
Question Submitted By :: Electrical-Engineering
I also faced this Question!!     Answer Posted By

# 1
UPS Battery Cacl:-

BATTERY RATING CALCULATION:-

The formula employed rating calculation is as stipulated
below :-

FORMULA EMPLOYED :

DC Current X Duration in Hrs
Capacity of Battery ( AH )=%age capacity utilization

UPS(KVA) x 1000 x Load Power Factor (=1)

Where , DC Current=Inverter efficiency x End Voltage

Hence , VAH = AH x Nominal Voltage

For e.g. : for 3 KVA UPS , 1 hour Backup :
3 x 1000 x 1
DC Current= 17.0 A
0.93 x 10.5 x 18
17.0 x 1.0
Battery ”AH “ = 27.4 AH
0.62
Hence , 18 nos of 12V/28AH batteries will suffice .

TOTAL VAH = 18 x 12 x 28 = 6048 VAH

The following assumptions have been made in the above
calculations :-

1. DC Voltage – 216 for 3 KVA
2. End cell voltage / battery of 10.5 V
3. Load Power Factor = 1.0
4. Inverter efficiency = 93%

% Capacity utilization is :

Duration % Capacity utilization

½ hr (30 mins) 52%
1hrs 62%
2hrs 74%
3hrs 83%
4hr 85%

For ups and invertor battery selection chart lOG On to:-

http://www.sharanapower.com/selection2.htm

 Is This Answer Correct ? 22 Yes 10 No
Thowsif_emerson_csm Team

# 2
9
 Is This Answer Correct ? 0 Yes 0 No

  Question Asked @ Answers Other Electrical Engineering Interview Questions what is the suitable voltage of transmission line to transmit 10000w power through 250 km. (a)11kv (b)33kv (c)66kv (d)132kv ]and please tell me whats the logic behind it ONGC 7 how to check the 3ph capacitor is good or not. MacLellan 14 Which of the following are the important limitations of rod gap surge arresters? 1. They are not capable of selling off power frequency follow up current. 2. After a discharge, the rods are destroyed completely. 3. Performance is affected by climatic conditions. Use the following codes for selecting the correct answer. Codes: (a)1, 2 and 3 (b)1 and 2 (c)2 and 3 (d)1 and 3 1 The iron loss in a 100kva transformer is 1 kw and full load copper losses are 2 kw, then what is maximum efficiency occure at a load? 3 dear sir, How i calculate the 2 phase welding transformer power or kva?? kindly tell me.... Gedco 2 How can i learn to programme every VFD. Or is there any typical study to understand VFD programming. Volkswagen 1 What are the different types of VVVF Drive ? 2 if we convert ampers into kwh or mwh ,which one formula use by us,pls tell me? 3 In what way does the variable ratio-arm improve the usefulness of the wheatstone bridge? 1 we change the speed of the synchronous motor by incresing or decreasing a rotor resistance 1 Elaborate the term "rotating magnetic field" APTRANSCO 1 how capacitor pass ac voltage practically?with increase frequency and cpacitance? DELL 1 For more Electrical Engineering Interview Questions Click Here