In core type transformers Each and every limb is ocupied with the both primary and secondary winding aree placed succesively arround each limb
In shell type ransformers is consturcted with the three limbs.
both primary ad secondary winding are wound around the central lmb..........
I have a 1000 kVA Transformer(11kV/0.415kV) and a APFC panel
of 400 kVAR(LT).Now if i want to remove the LT APFC panel
and install a HT(11kV) APFC panel on the HT side is the HT
APFC panel will work same as the LT APFC panel(improve the
power factor),if yes what will be rating of the HT APFC
panel?what is the formula to calculate HT APFC panel rating???