In core type transformers Each and every limb is ocupied with the both primary and secondary winding aree placed succesively arround each limb
In shell type ransformers is consturcted with the three limbs.
both primary ad secondary winding are wound around the central lmb..........
I have 4 DG set with 1500KVA rating. system breakers are
11KV & alternator are 415 Volts. i want to Know what is
max. resistance for body earthing & 415 & 11KV V Neuteal
earthing. my fault current is 14 times for 2 sec.