| Other Electrical Engineering Interview Questions |
|| Asked @
|what is Diversity factor in electrical installations
|IN MY INDUSTRIES 125 HP MOTOR USED FOR THAT ONLOAD AMPS UP
SO CAN I USE ONE LOWER KVA DG SET WITH STEP UP TRANSFORMERS
THAT MEANS WITH LOW POWER INPUT TO GET CONSTANT HIGH POWER
EG:125KVA DG SET = 250 KVA STEP UP TRANSFORMERS
|what is the value of current as well as voltage upto which
we will not feel shock and why?
|Why Diffrential and Ref relays are used together although
Diffrential relay can protect Pri and Sec of Transformer
|DRAW THE DIFFERENCE BETWEEN GROUND AND NEUTRAL IN BOTH
SINGLE PHASE AND THREE PHASE?
|HOW GENERATING END VOLTAGE LEVEL (6.6 KV/ 10.5 KV/ 11 KV/
13.5 KV) DECIDED IN POWER PLANT. ON WHAT FACTORS THE
GENERATING END VOLTAGE DECIDED, & WHAT IS THE CALCULATION
USED FOR THIS.
|what is the difference between relay and a contactor.
|what is the basic difference between synchronous
motor,synchronous generator and induction motor
|why total tape position are odd in number in Power
|Why Nutral CT rating for Earth Fault Protection of Transformer neutral shall be 20% of Full load Current of Transformer
|Is pure capacitor load and pure inductor load is an linear
load? pls justify
|what is the current rating of 2500 KVA,33KV/433v transformer
on secondary(LT) side
|For more Electrical Engineering Interview Questions Click Here |