cvt is capacitive voltage transformer this is using from
PT potential transformer this is using upto 132KV level
beyond this PT is not economical. CVT and PT both r step
down transformer. both r using measuring and protection
purpose but CVT we can use communication purpose.in CVT
capacitor acting as a potential divider.
CVT means capacitive voltage transformer
PT means potential transformer
both are same in view of votage measurment
CVT is used in the line ckt while PT is used in the bus Ckt.
for ur kind informtion CVT may be used as PT but PT can not
be used as CVT as per .
1- Inductive Voltage Transformer (VT or PT)
2- Capacitive Voltage Transformer (CVT)
The main difference between VT and CVT is that the CVT is
based on capacitive voltage divider principle which steps
down the high voltage to a lower voltage level that can be
measured easier. This can make the VT much less bulky (save
space) and also less expensive. This is why that for voltage
levels up to 132 kV, itís common to use conventional VTs but
at voltage levels more than 132 kV we use CVTs.
Generally the PT or CVT are used to measure voltage.
The secondary of the PT will be 110V which will be connected for the voltage measurement. For high voltage applications like 132 or 230 or 400kV. Designing the PT for 132 to 110V will be very bulky and practically leads to very big size.
Hence for high voltage applications we use CVT. The CVT is constructed using serious of capacitors. Consider we are connecting 10 capacitors of equal rating in series. Hence the voltage along the capacitors are equal we will take output of one capacitors are connect it to a PT and secondary of PT 110V will be used for measurement.
VT and CVT are besically use the same fundamental physics for measure the voltage at sedondary as according to its primery..but the besic diff. Is VT usually use for measurement to voltage for protection ckts as well for metering purpose, CVT also can be use for the same purpose but additional advantage with CVT is it can be use in communication purpose as it does have the capacitors as a fliter who can diff. The communication signals and protection signals or you can say tele protection also the purpose depands on the classes of VT and CVT as according to requirement of protection and communication like over voltage pro. Distance pro. Or metering as per requirement
it is connected bet communication wavedrop and Ct.it is
used for met &pro..it is nothing but acapacitor arrangement
due to this large level of voltage will be stored and due
to small stepdown transfomer inside it is reduced to as
CVT means capacitive voltage transformer which is connected
between the lightening arrester and CT,which is used to
measure the voltage in the line in higher ratings,PT is
connected at the end of the bus bar system which is also
used to measure the voltage.
We have 2 11kv/433v transformers for 2saperate acb for mv
panels and 1 bus coupler acb. Suppose Iíll close bus
coupler what will happen or it will be share the load.
Please suggestion and any modification required.
For polarity test on a 11/3.3kV 2.5MVA delta-star Unit
Auxiliary transformer,415V 3-phase supply was applied at
the HV. Connection between Aa was made with a 2.5mm cable.
As soon as power was switched on the cable caught fire and
burnt. This test was then abandoned. It is noteworthy to
say that a similar cable was also used in a similar
transformer for the same. The cable did not burn and test
was successfully completed with good result. What is wrong?
Please, help me out.