Dyn11 is vector group notation of tansformer.It means LV
winding,which is star connected (written in small letters
means LV side and vice versa)is 30 degrees lagging by HV
winding which is delta connected.In India we go for +-30
deg connection of transformer.
D = Delta connection at primary,y = Star connection at
secondary and n = neutral point connected at secondary.
Dyn 11 means that the voltage of the secondary star winding
lead the primary phase voltage by 30 degree and it
corresponds to 11 o'clock.
Dyn11 means the Low Voltage winding is Delta connected and
High Voltage winding is Y connected with neutal is being
brought out. 11 shows that the LV winding is leading HV
winding by the angle of 30 degree.
First symbol/symbols, capital letters: HV winding connection.
Second symbol/symbols, small letters: LV winding connection.
Third symbol, number: Phase displacement expressed as the
clock hour number.
Winding connection designations
High Voltage Always capital letters
Delta - D
Star - S
Interconnected star - Z
Neutral brought out - N
Low voltage Always small letters
Delta - d
Star - s
Interconnected star - z
Neutral brought out - n
Phase rotation is always anti-clockwise. (international
Use the hour indicator as the indicating phase displacement
angle. Because there are 12 hours on a clock, and a circle
consists out of 360°, each hour represents 30°.
Thus 1 = 30°, 2 = 60°, 3 = 90°, 6 = 180° and 12 = 0° or 360°.
The minute hand is set on 12 o'clock and replaces the line
to neutral voltage (sometimes imaginary) of the HV winding.
This position is always the reference point.
Because rotation is anti-clockwise, 1 = 30° lagging (LV lags
HV with 30°)and 11 = 330° lagging or 30° leading (LV leads
HV with 30°)
Delta connected HV winding, star connected LV winding with
neutral brought out, LV is leading HV with 30°
An 11kv system consisting of an underground cable to a sub
station about 300 meters away was shut down for about 10
hrs. On energising, it tripped off on earth fault about
10---20 mins later 6 times but since than it is not
tripping.its already 3 weeks now. The SPAJ was found to be
fine. what could be the cause.No test had been done to
determine the cause of the trippings till now because of