Hi frnds :)
plz tell me that i have 100 KVA 3 phase generator so by
thumb rule 100*1.4 = 144 amps
and generaly we can operate at 80% load...so it will 144*0.8
so now i m confused about single phase load.....if we use
that generator only for single phase the that 112 amps is
total single phase load or i can give 112 amps at red 112
amps at yellow and 112 amps at blue....
i mean that total single phase load that 100 KVA generator
will take is 112+112+112=336 amp ??
while calculating demand in my company the present load in
kw is 212.... there 125kvar capacitor bank is installed by
spliting as 50 in departments...the diasplay in panek biard
shows 175kw... how could we know the amount of kvar used to
compensate the kva