Power factor is the cosine factor of the voltage & current
phase difference. Its a short defination. But if you go
deeply, Power factor=cos@,its depend only on load, instead
of phasewise.if you connect same load in every phase it
will show same power factor value in each phase.Because
power factor is depended upon load resistance=R & its
impedance=Z,

cos@ = R/Z,

So if you are going to calcualte the power factor of all
phase, you have to calculate all resistance & impedance of
the load. Then you can calulate the avg. power factor.

R=R1+R2+R3
Z+Z1+Z2+Z3

(Where Z=R+jXL=Impedance)

cos@=R/Z

Hope my answer will satisfy you.

Best Regards,
Engr.Abdurrahim
shaikh337@rediffmail.com

Dear all,
This is not an answer, actually question.

In one factory, we are dificult to measure resistance,R and
impedance, Z.

What we have is only voltage supply (3phase, 420volt), and
total current flow during maximum usage using clampmeter
(including machinery, lamp, computers, etc...)

We also have info of main transformer step down because it
is in the factory area. Normally they stated value of KVA.

And some factory already install the 'capasitor bank
regulator'

So, how we can calculate the CORRECT VALUE of capasitor
need to install?

I mean, which one is the correct KW, which one is the
correct KVA, and how to calculate existing power factor IF
the factory already have 'capasitor bank regulator'....can
we switsh of the regulator?

By using sequence components ... (+vesequence power - -ve
seq power)/VA

Is This Answer Correct ?

0 Yes

4 No

Reddy

Other Electrical Engineering Interview Questions

Question

Asked @

Answers

I have a shop heater with a 1/3 hp capacitor start,
induction motor driving the fan. Intermittently, the fan
motor speeds up significantly for several seconds (15-60
sec) then slows to normal operating speed. The manufacturer
suggested changing the capacitor which made no sense, but I
did it to no avail.
Could this possibly be caused by the centrifugal switch
intermittently reconnecting the start winding?

Hello friends i am facing one problem in lighting panel.
Frequently neutral link near to MCCB is burning(firing. What
may be the reason for this one. Please answer me.

my UPS is 600VA with 0.6 p.f
and i use it for my computer which has 450W power supply
unit, a monitor of 633nW and speakers.
Can any one explain this..
because the output of UPS should be 360W (<450W)

Kindly give the brief explanations for checking 12.5 kvar
440V, 25 KVAR 440V, 12.5KVAR 690V, 25 KVAR 690V capacitors
microfarad values. what is the microfarad values for the
above four type of capacitors, and give the formula
explanations briefly. I know F-50HZ, voltage, and capacitor.