The busbar size will be determined by the total loads
connected to the bus.This will require a comprehensive
study of nature of loads plus the surroundings of place.
The general procedure will be such that the operating
parameters don't voilate the maximum safety limits of the
busbar sizes can not be calculated only from overall size.
there are various derating factors like arrangment of
busbar, nos of busbar, spacing, enclouser size, ventilation
in room, temp rise, skin effect, proximity effect etc.
which need to be consider while designing the busbar.
Usually busbar sizes selection depends mainly on two
factors. Which is current + temperature. The size which you
are going to select must carry the current you need and
must not create much heat which excess the limits.
There is one 40MVA oil cooled transformer (yet to
commission), filled with 95% oil and we are trying to fill
5% Nytrogen in that transformer so that there should not be
any foreign component inside. But even though there is no
leakage, nytrogen is not withstanding inside transformer,
within a day or two pressure guage is showing 0. Why is it
soooo? Pls reply.
The power showed in the name plate of the motor is input
power or output power??
The power showed in the name plate is 18.5kw
measured current is 34.5 amps. location is india.
can i calculate the efficiency of the motor using this
in thermal power plant the steam produced is made to cool
after falling on the turbine blades.
my question is why this is done while the same is needed to
heat up again.
"jab pani ko wapis garam hi karna hai to thanda kyu karte