| Other Electrical Engineering Interview Questions |
|| Asked @
|On load tap changer (OLTC) explode?
Vector group: Ynd11
Rated Power: 353MVA
Rated Current: 693A
Type: T III Y1000 110/c 12193w
Max Operation Current: 295A
Step Voltage: 550V
Arrangement in Tx windings: Y Connection
Problem: Damage of Unit 1 Generator Transformer On Load Tap
Description of Incident:
9.00 a.m. :- Generator No Load test on excitation system
10.30 a.m :- Carried out AVR change over
11.30 a.m :- Preparation for Generator Manual Synchronizing
12.00 a.m :- Manual Synshronizing test started.
Observed incoming generator voltage higher than running voltage.
CECR operator operated Generator Transformer OLTC to bring down
the incoming generator voltage
12.03 a.m :-Generator Transformer abnormal alarm operated at
Gen.Control Desk (CECR)
CECR operater at Generator transformer bay informed that the
oil splashed out from OLTC.
CECR operater informed that he heard explosion inside OLTC.
Observed Oil level & Oil Flow alaram operated at Tranformer
12.05 am :- CECR operator 'Open Gen Field Breaker”
12.10 a.m. :- Elec1 team inspected the OLTC and found the
OLTC rupture disk was broken
and oil spilled at OLTC area.
- Elec1 found the OLTC top cover bulging.
Do anyone know why and possibility cause happen in this OLTC.
|why transformer is rated in KVA ?
|how to converate kva to kw ?
|How can we calculate the cable size???
plz give the formula !!!!!
|How we can design a cable for a 3phase load.
|difference between brush less & brush excitation in a
|WHAT IS THE DIFFERENCE BETWEEN A DC MACHINE OUTPUT AND
|Ferranti Effect says that voltage at the receiving end is
higher than that at the sending end. How is it possible?
|why r use the wave taper in the substation ?
|What is switch gear? How it is work ?
|Why P.f. of the system decreases when it is connectect
across induction motor? & how to maintain the p.f. of
system to unity.?
|how can we calculate the current
|For more Electrical Engineering Interview Questions Click Here |