In usual practice, the carrying capacity of copper is taken
as 2.5 A/sq mm and 1.5 for Al.If the load is steady and
continuous 60 % of these values are adopted.

There is no formula for calculating the cable size. Usually
the cables are sizing based on standards like NEC,BEC.,
etc. if you want to size the cable you first choose the
std, which is using in ur location.as per NEC std just
multiply the 100*1.25=125A, choose the cable ( table-
310.16) for that size. after you choose the cable you have
to derate the cable for your laying location & way of
laying.

Theory for Cable Sizing.
From Ohms law, the voltage drop in an electrical conductor is
V = I R
where
I = Current, amps
R = Resistance, Ohms

The electrical resistance can be derived from the properties of the conductor material.
R = ρ L / A
where
ρ = Resistivity, Ω mm2 /m
L = Length, m
A = Cross sectional area, mm2
Watch the units in the above equation.

The resistance can also be expressed in terms of the material conductivity (ψ) which is just the reciprocal of the resistivity.
R = L / (ψ A)

Table 1. Typical material electrical conductivity
Material Conductivity, ψ
Copper 58
Aluminium 36
Mild Steel 7.7

Combining Ohms law with the resistance expression, we get.
V = (I L) / (ψ A)

Now, we can define an acceptable voltage drop in a conductor. I have calculated the voltage drop that was used in several published tables and get around 5.5 Volts.
We could therefore re-arrange this equation to give the cable size. But cables come in standard sizes measured in mm2. In addition, you also need to consider the maximum current for each cable size.

Table 2. Conductor sizes and maximum currents
Cable Size, mm2 1.5 2.5 4 6 10 16 25 35 50 70 95 120 150 185 240 300
Maximum current, A 13 21 28 36 46 61 81 99 125 160 195 220 250 285 340 395
So, the theory is relatively simple, let us now see how to use the program.

there is no funda or formula to get size of conductor wrt
to load. just calculate the ampere of the load, and then as
per ampere ,,, as per the cross sectional area of the
conducter like 1.5mmsq can bear the 4-6amp load,,,so on..

Is This Answer Correct ?

4 Yes

16 No

Amrish Sharma

Other Electrical Engineering Interview Questions

Question

Asked @

Answers

how techometer works and how it will be connected above the
flywheel in dg system

We have 800KW motor operating at 6600Volt,50 Hz
supply.During 1st startup it tripped on overcurrent
trip.It's FLA is 88 Amps.The K factor of Thermal overloaaad
was set on .94 initially.then we set at 0.97 and then it
started fine.i dont understand why it tripped first?What
are the protections which comes in picture during starting ?